Originally Posted by dcheatwood
Yep got me twice before I figured it out. Open valve so slow, you should hear a little squeal as the lp starts to flow. When noise stops, pressure has equalized and you can open it on up.
But if stove flame is normal height this is not you problem. Check flame with all burners on. If flames are strong, ?????
I had it happen "ran out of fuel" and installed full tanks and consequently opened valves to fast then popped opd valve.
Stove burners still worked but a lower flame.
Did as I said in previous post and all was fine.
Goshen is my playground.
The last man standing also has a sharpie