Originally Posted by tylerochoa24
It's a 50 amp. Plugs in on both ends.
Ok, it sounds like you possibly have a multi-meter with you. You will need to check both legs of 120 volts (you have two legs on a 50 amp split phase 120/240 volt service).
I would advise checking the power pedestal first. If all is good there, the attach the cord to the pedestal (but not to the RV), then check the cord end that plugs into the RV for same.
If both of those check out, then we can troubleshoot further. make sure you flip the circuit breaker at the pedestal off when attaching/detaching the cord.
Using this link, click on the 'outlet testing' tab on the left. It will have diagrams to show you the voltages you should be getting between all the tabs.
And you are not using any adapters, correct?