Wife went to take shower and no hot water. I checked outside at the girard unit and it has a steady led light. In the manual it says that is a - internal control fault. Tried the 800 number and office is closed. Has anyone had this issue and if so is there anything I can do to fix it?? Any help would be appreciated.
Not sure what the problem was. I did a google search and found the service manual. I only got a junky brochure when I purchased. I did all the recommended troubleshoot items and it finally worked. I did notice the sail switch was sticking and not moving freely. So maybe that was the culprit.